Wentworth House Rail Systems undertook the required survey during a night time possession and isolation of the up slow line. The survey required both the vertical and horizontal distance measurement of the Return Conductor from the Up Slow line cess rail at 2 m centres using a laser measure and swivel gauge. The survey measurements were superimposed on to the topographical survey drawing and the proposed multi-storey car park general arrangement and elevation drawings. From the resulting clearance drawing it was confirmed that the proposed multi-storey car park was sufficiently clear of the return conductor that no remedial action was required.
WENTWORTH HOUSE RAIL SYSTEMS
Wentworth House Rail Systems is a leading provider of Overhead Line (OLE) Design and Consultancy services.
- About Us
- Modern Slavery and Human Trafficking Policy